Hangers shall be as described in 30N spec, but they shall be pre-compressed and locked at the rated deflection by means of a resilient seismic up stop to keep the piping or equipment at a fixed elevation during installation. The hangers shall be designed with a release mechanism to free the spring after the installation is complete and the hanger is subjected to its full load. Deflection shall be clearly indicated by means of a scale. Submittals shall include a drawing of the hanger showing the 30 degree capability. Hangers shall be type PC30N as manufactured by Mason Industries, Inc.
|SIZE||Rated Capacity (Ibs)||Rated Defl (in)||Spring Constant (Ibs/in)||MRD (in)|